I just connected 9 dimmers and 1 4PD to my Velbus and so connected to my PC via USB.
With 1 dimmer and 4PB in test setup everything worked, but now I get the following error:
the velbus network could not handle the current trafic load and has entered an erroneous state
I doublechecked the cabling everythings seems to be OK…
I can’t find anywhere some information about this error.
I suppose you’ve already checked this, but just to remind you: don’t forget to check the terminator dip switches …
Yes indeed I checked already… There is only 1 dip switch set on the 1 module at the end of the longest cable being the 4PB. All 9 dimmer modules are in the cable room with dip switch.
Just to let you know that I found out what was the problem. There was 1 really tiny small copper wire that was making a short curcuit on the bus on my 8th dimmer.